Press Release Date:
July 12, 2007
Airflow Simulation Ensures +/- 1° F Temperature Range in Pharmaceutical Warehouse Preserving Life-Saving Drugs
(July 12, 2007) -- Flomerics' consultants used their Flovent software to evaluate design alternatives which helped Eichleay Engineers
Inc. of California design an air handling system that keeps temperatures in a pharmaceutical warehouse within ±1Airflow Simulation
Ensures ± 1° F Temperature Range in Pharmaceutical Warehouse Preserving Life-Saving Drugs F. Flomerics' consultants evaluated
design alternatives and identified a fan configuration that met the pharmaceutical company's requirements for both temperature
variation and air velocity. "The HVAC system has been in operation for over a year and the temperatures in the warehouse have never
been outside the customer's specified range," said Michael Simpson, Mechanical Engineer for Eichleay Engineers.
A pharmaceutical warehouse contains 49,200 square feet of warehouse storage space and has a roof height that varies from 25 to 28
feet. In order to maximize the life of the product stored in the facility the client established a requirement that the temperature
throughout the entire interior space be held between 67o F and 74o F and at less than 50% relative humidity. "We began the project by
using standard computer calculations to design an HVAC system that was capable of keeping the temperature in the building at the
required level," Simpson said. "This system could get us to the right average temperature but left us with very little safety margin."
"We called the two leading software companies in the HVAC CFD industry. We knew that they both offered people with extensive
experience in air flow simulation modeling. One of the companies told us that we would have to wait several weeks before they could
even take a look at our problem. On the other hand, Flomerics told us they would be there the next day to give us an estimate and get
started on our project." Flomerics' consultant Chris Wark simulated the existing building and several alternatives using different types
of fans. He found that the addition of 50 Airius® Destratification fans reduced the temperature variation within the building to
a ±1Airflow Simulation Ensures ±1° F Temperature Range in Pharmaceutical Warehouse Preserving Life-Saving Drugs F
The building's HVAC control system was designed to issue an alert to plant operating personnel whenever temperatures in the space
fall outside a ±3.5 o F limit from set point. "The new HVAC system has been up and running for about 18 months and since then, the
temperature alarms have not shown any excursions," Simpson said. Most importantly, the customer is extremely pleased that the
building has met their requirements."
For more information, visit Flomerics' Web site at http://www.flovent.com
Flomerics Inc. US Headquarters 4 Mount Royal Ave., Suite 450 Marlborough, MA 01752 Tel: +1 (508) 357 2012 Fax: +1 (508) 357
2013 E-mail: [email protected]
Web site: www.flomerics.com
FLOMERICS LIMITED 81 Bridge Road o Hampton Court Surrey KT8 9HH o England Tel: +44 (0) 20 8487 3000 E-Mail: [email protected]
4 Mount Royal Ave.
Marlborough, MA 01752
News provided by ThomasNet Industrial Newsroom® (TIN). TIN is a comprehensive source of new and timely product information in the industrial marketplace. TIN supplies new product information to the Web sites, e-marketplaces and print publications that serve the industrial marketplace.
IL GLAUCOMA I GLAUCOMI PRIMARI . 3 GLAUCOMA SECONDARIO AD ANGOLO APERTO . 3 GLAUCOMI SECONDARI DA CHIUSURA D'ANGOLO . 4 Anatomia e fisiologia della produzione e deflusso dell'umore acqueo . 6 Anatomia e vascolarizzazione della testa del nervo ottico. . 7 Teorie patogenetiche del danno glauacomatoso . 8 In generale . 9 -Tonometria . 9 Oftalmoscopia . 10 Esame dello strato delle fibre nervose
DA DECLARAÇÃO DE INCONSTITUCIONALIDADE DO ART. 273, DO CÓDIGO PENAL OU RECONHECIMENTO DA ATIPICIDADE MATERIAL DO FATO, ANTE A INEXISTÊNCIA DE RESULTADO JURÍDICO Por Bruno Haddad Galvão, Defensor Público do Estado de São Paulo O artigo 273, do Código Penal, foi introduzido pela Lei 9.677, de dois Assim como outras leis, tais como a de n.° 8072/90 e 8930/94, referida lei foi